Air Conditioning Repair and Maintenance: Carry out preventative maintenance on office aircon units and remaining running freezer unit. Clear all drains, Clean condensers, Clean all filters, Check all evaps,-all ok.
Air Conditioning Faults to report – Freezer room lights not working, checked over circuit, found hot join in j-box shorting circuit. Re-terminated, tested, lights now working. Freezer unit 2 is short of gas due to suspected leak in deteriorated condenser coil and has been isolated.