Air Conditioning Repair and Maintenance: Carry out preventative maintenance on office aircon units and remaining running freezer unit. Clear all drains, Clean condensers, Clean all filters, Check all evaps,-all ok. Air Conditioning Faults to report – Freezer room lights not working, checked over circuit, found hot join in j-box shorting circuit. Re-terminated, tested, lights now…
Air Conditioning Maintenance: Isolated Daikin unit at the switch board, removed cover, drain pan and replaced drain pump. Put unit back together, turned on and all working fine.
Air Conditioning Maintenance: Found front defrost heater to be faulty replaced heater and tested all working well.
Air Conditioning Maintenance: On all site air conditioning including cleaning all condensers and return air filters and sucking all drains, found all 4 units need a coil clean.
Air Conditioning Maintenance: Included filter and belt change, clear drains, evaporative coil, condenser unit. All working well.